Cylindrical post top luminaire consists of base with shade supported by four stainless steel support rods. Heavy-duty cast aluminum base with integral slip fitter anchors the support rods, and is machined to include groove for gasketing and mounting surface for the lens and ballast enclosure. Shade shall be spun aluminum and free from burrs and sharp edges. Shade and base are gasketed to provide a weather-tight seal to the clear acrylic cylindrical lens. Luminaire slip fits 3" O.D. pole or tenon, and has built-in stop to limit insertion depth to 3.5". Two offset rows of three 10mm recessed setscrews secure the luminaire to the pole. All hardware is stainless steel.
Vertical base down lamp is positioned within the clear cylindrical acrylic lens. Underside of shade is painted white. Optional internal louvers are available for symmetric and asymmetric distributions to provide brightness control.
Electrical components are mounted in a conical spun aluminum enclosure at the base of the luminaire. Enclosure is painted white. Optional quick disconnect for tool-less replacement of ballast pod available on request.
Metal halide core and coil ballast with class "H" (180?C) insulation system shall have a minimum high power factor rating of 90% and nominal ballast factor of 1.0. Ballast shall be capable of reliable starting to -20?F (-30?C) at nominal line voltage of ?10%. Ballast and capacitor are UL and CSA recognized. Mogul base porcelain socket for 200w pulse start metal halide is 1500w-600v, 4kV pulse rated. Medium base porcelain socket for 150 ceramic metal halide is 660w-600v, 4kV pulse rated.
150w ceramic metal halide - MHC150/C/U/M
200w pulse start metal halide - MS200/C/V/PS/737
Wattage: Internal Louver / Asymmetric Louver
150 watt: B3-U5-G3 / B2-U5-G3
200 watt: B3-U5-G4 / B3-U5-G4
Fabricated steel bracket assembly mounts over junction box and is secured to the wall in four places by customer supplied hardware. Two parallel square tubes with 3" O.D. tenon are welded to the 0.24" thick mounting plate. Mounting bracket is hot-dip galvanized with coating inside and out, then lightly sanded prior to painting. Bracket assembly ships prewired with fish tape.
Housing is cleaned ultrasonically prior to painting. Standard finish is finely textured matte silver grey metallic or black. Special colors available on request.
INGRESS PROTECTION: IP54
CERTIFICATION: UL Listed for Wet Locations
Limited product warranty period is three years. Lamp and ballast shall carry the respective manufacturer's limited warranty.