Cylindrical post top luminaire consists of roof, shade, and external louvers with matching profiles. Four stainless steel upper support rods separate the heavy-duty cast aluminum roof and spun aluminum shade, forming an aperture at the top of the luminaire. Machined lower rods support the shade and retain three spun aluminum external louvers midway along its length. Shade and louvers shall be free from burrs and sharp edges. Heavy-duty cast aluminum base with integral slipfitter anchors the support rods, and is machined to include groove for gasketing and mounting surface for the lens and ballast enclosure. Roof and base are gasketed to provide a weather-tight seal to the clear acrylic cylindrical lens. Luminaire slip fits 3" O.D. tenon, and has built-in stop to limit insertion depth to 2.8". Two offset rows of three 10mm recessed setscrews secure the luminaire to the pole. All hardware is stainless steel.
Vertical base down lamp is positioned within the clear cylindrical acrylic lens. Three external louvers, painted to match the fixture, shield the lamp at normal viewing angles. Underside of spun aluminum shade and roof are painted white. Optional internal louvers are available for symmetric and asymmetric distributions to provide additional brightness control.
Electrical components are mounted in a conical spun aluminum enclosure at the base of the luminaire. Enclosure is painted white. Optional quick disconnect for tool-less replacement of ballast pod for 70w and 100w is available on request.
70 watt and 100 watt ceramic metal halide electronic ballast shall be Sound Rated A and Outdoor Type 1 rated. Ballast shall have a minimum high power factor rating of 97% and nominal ballast factor of 0.99. Total harmonic distortion shall be less than 10%. Ballast shall be capable of reliable starting to -20°F (-30°C) at nominal line voltage. Ballast is UL and CSA recognized. G12 base porcelain socket is 660w-600v, 4kV pulse rated.
150 watt ceramic metal halide core and coil ballast with class "H" (180°C) insulation system shall have a minimum high power factor rating of 90% and nominal ballast factor of 1.0. Ballast and starter combination shall be capable of reliable starting to -20°F (-30°C) at nominal line voltage of ±10%. Ballast, capacitor, and starter are UL and CSA recognized. Medium base porcelain socket is 660w-600v, 4kV pulse rated.
70w ceramic metal halide - MHC70/C/U/M/3K
100w ceramic metal halide - MHC100/C/U/M/3K
150w ceramic metal halide - MHC150/C/U/M/3K
Wattage / No Louver / Internal Louver / Asymmetric Louver
70w: B1-U3-G2 / B2-U3-G2 / B1-U3-G2
150w: B3-U3-G3 / B3-U3-G3 / B2-U3-G3
Fabricated steel bracket assembly mounts over junction box and is secured to the wall in four places. Two parallel square tubes with 3" O.D. tenon are welded to the 0.24" thick mounting plate. Mounting bracket is hot-dip galvanized with coating inside and out, then lightly sanded prior to painting. Bracket assembly ships pre-wired with fish tape.
Housing is cleaned ultrasonically prior to painting. Standard finish is finely textured matte silver grey metallic or black. Special colors available on request.
LUMINAIRE WEIGHT: 29 lbs
LUMINAIRE EPA: 1.9 sq ft
INGRESS PROTECTION: IP54
UL Listed for Wet Locations
Limited product warranty period is three years. Lamp and ballast shall carry the respective manufacturer's limited warranty.