Luminaire base with integral fitter is cast aluminum and is secured to pole top with three recessed setscrews. Clear acrylic cylindrical lens with integral reflector twists and locks onto housing without the use of tools providing access for relamping. Satin anodized rings encircle the reflector as a decorative element. Electrical gear is located in the luminaire base.
Vertical base down lamp is positioned within facetted aluminum reflector for optimal performance. Reflector material is textured to reduce brightness. Specify Type V or Type III distribution.
Ceramic metal halide electronic ballast shall be Sound Rated A and Outdoor Type 1 rated. Ballast shall have a minimum high power factor rating of 97% and nominal ballast factor of 0.99. Total harmonic distortion shall be less than 10%. Ballast shall be capable of reliable starting to -20°F (-30°C) at nominal line voltage. Ballast is UL and CSA recognized. Porcelain socket is 660w-600v, 4kV pulse rated.
70w T6 / G12 base ceramic metal halide
39w T6 / G12 base ceramic metal halide
70w Type V: B2-U3-G1
70w Type III: B2-U3-G2
39w Type V: B1-U3-G1
39w Type III: B1-U3-G1
Upper shaft of laddered aluminum pole and integral bracket arms are fabricated from two parallel 0.114" thick rectangular tube sections separated by horizontal plates welded at evenly spaced intervals along the length of the shaft. Bracket arms have integral tenon to accept luminaires. Flush mounted hand hole cover is plasma cut with kerf not to exceed 1/8" and includes triangular tamper-resistant locking device. Nominal pole height is 12'. Pole ships pre-wired with fish-tape.
Housing is cleaned ultrasonically prior to painting. Standard finishes are finely textured matte silver grey metallic, dark grey, graphite grey, matte black, or dark bronze. Special colors available on request.
LUMINAIRE WEIGHT: 25 lbs
LUMINAIRE EPA: 1.5 sq ft
INGRESS PROTECTION: IP65
CSA/US Certified for Wet Locations
Limited product warranty period is three years. Lamp and ballast shall carry the manufacturer's limited warranty.