One-piece luminaire base and top are precision-machined from 6060 billet aluminum, then satin anodized. Conical matte acrylic lens is mechanically secured to the base with retaining ring and two concealed socket head cap screws. One-piece neoprene gasketing provides a weather-tight seal. Luminaire base fastens to the one-piece cast aluminum tapered housing with three recessed setscrews and is sealed with one-piece closed cell silicone gasket. Electronic ballast mounts to plate on the underside of the base and is housed in the top of the housing. All hardware is stainless steel.
Vertical, base down lamp is positioned within the cylindrical matte acrylic lens producing symmetrical distribution.
Compact fluorescent high frequency electronic ballast shall be Class P and Outdoor Type 1 rated. Ballast shall have a minimum high power factor rating of 90% and a minimum starting temperature of -20°F (-30°C) at nominal line voltage ±10%. Ballast shall be UL Listed. Lamp sockets are 75w-600v rated.
LAMPING / BUG RATING
26w PL-C - CFQ26W/G24q/835 - B1-U3-G1
32w PL-T - CFTR32W/GX24q/835 - B1-U3-G1
42w PL-T - CFTR42W/GX24q/835 - B1-U3-G2
Inverted tapered bollard shaft with integral flange plate is cast aluminum with nominal wall thickness of 0.24''. Bollard shaft mounts to anchor base plate assembly with four M10 x 20mm stainless steel socket head cap screws. Anchor base assembly consists of four 3/8'' x 10'' x 1-1/2'' hot-dip galvanized anchor rods secured to a mounting plate and embedded as an assembly in concrete foundation (by others). See pole data sheet for mounting details.
Housing is satin anodized aluminum. Standard finish for bollard shaft is finely textured matte silver gray metallic. Special colors available on request.
Limited product warranty period is three years. Lamp and transformer shall carry the manufacturer's limited warranty.